This tech-tip is meant to give to give some suggestions for installing wireless AC current meters for your application. For product documentation and additional help visit www.monnit.com/support.
Before Mounting Your Sensor
Before mounting your sensor, add the sensor to your iMonnit account. Sensors must be registered to a gateway to be operable. Registering your sensor(s) and Gateway(s) is easier than ever before with iMonnit mobile. You can just scan a QR code and have your ID and Security code entered automatically.
From the overview page, select Add Device.
You will need to enter the Device ID and Security Code from your MonnitLink™ gateway in the corresponding text boxes.
Use the camera on your smartphone to scan the QR code on your Gateways(s) first. Then scan your sensor(s).
If you do not have a camera on your phone or it is not accepting the QR code, you may enter the Device ID and Security Code manually.
The Device ID is a unique number located on each device label. It will be labeled as “ID” on your MonnitLink™ gateway or Monnit sensor.
Next, you'll be asked to enter the Security Code (SC) on your device. A security code will be all letters, no numbers. It can also be found on the barcode label of your MonnitLink™ gateway Or Monnit® sensor.
When you are finished adding the sensor to your account, insert the battery. Peel back the black sticker cover of the battery slot and slide the coin cell battery into the sensor as shown in the following illustration. The sensor will power within 10-20 seconds. Once online, your sensor is ready to be deployed.
Placing and Mounting the Sensor
Monnit wireless AC Current Meters measure the RMS current of an alternating current (AC) system using a current transformer (CT) that wraps around the "hot" wire of a two-wire (hot, common, ground (optional)) power system. Monnit wireless sensors feature mounting flanges and can be attached to most surfaces using the included mounting screws or double-sided tape.
Proper Antenna Orientation for Optimal Operation
To get the best performance out of your Monnit Wireless Sensors, it is important to note proper antenna orientation and sensor positioning. Antennas should all be oriented in the same direction, pointing vertically from the sensor. If the sensor is mounted flat on its back on a horizontal surface, you should bend the antenna as close to the sensor housing as possible giving you the most amount of antenna pointing vertically. You should make the antenna wire as straight as possible, avoiding any kinks and curving of the wire. Sensors must be at least 3 ft. away from other sensors and the wireless gateway to function properly.
Configure the Sensor Settings in Software
To edit a sensor’s operation settings, click on the sensor overview row to display the details view. Click on the “Edit” tab to access the sensor configuration panel.
The sensor edit panel allows you to set the primary configurations for the sensor. Mousing over the question mark icon by each set will explain that setting. When you have finished making changes, press the “Save” button at the bottom of this section.
Note: Be sure to click the “Save” button anytime you make a change to any of the sensor parameters. All changes made to the sensor settings will be downloaded to the sensor on the next sensor heartbeat (check-in). Once a change has been made and “Saved,” you will not be able to edit that sensor’s configurations again until the sensor has downloaded the new setting.
For information on setting up sensor notifications view the following knowledgebase article, https://www.monnit.com/support/setup/getting-started---actions